The boiler feed booster pumps are installed upstream of boiler feed pumps to deliver feed water with the pumping temperature of max. 165°C at the power units in TPS’s to ensure a cavitation-free operation of the main pumps.
PD 650-160: motor-driven horizontal single-stage axially split (radially split in case of PD 650-160-2) volute-casing centrifugal pumps with a double entry radial impeller. Pump nozzles oriented horizontally to the opposite sides. The pump rotor is carried by the oil-ring lubricated plain bearings. Shaft sealing: packed glands.
PD 1600-180-2: turbine-driven horizontal single-stage radially split volute-casing centrifugal pumps with a double entry radial impeller. The discharge nozzle horizontally sideward, the suction nozzle vertically to the bottom. The pump rotor is carried by the pressure lubricated plain bearings. Shaft sealing: mechanical seals.
|Nos||Pump make||Capacity, m3/h||Head, m||Ratational speed, rpm||Motor
|1||PD 650-160||650||158||3000 (synchr.)||324|
* for TPS 800 MW power units
** for TPS 500 MW power units
*** for TPS 320 MW power units